Hello, I have recently purchased the NFPA 36, but i could not find what I was looking for. Basically I was looking for steps to control fire inside solvent extraction DT [Desolvantizing Toaster Equipment]. We have Steam Fire Extinguisher System, but I am asking in case this fails what to do?
Hi everyone. Is this neccessary to consider interface between Fire Alarm System & room HVAC system? while 2-1.13 of nfpa 91 says:" Fire detection and alarm systems shall not be interlocked to shut down air-moving devices." On the other hand, 21.7.3 of NFPA 72: Connections between fire alarm systems and the HVAC system for the purpose of